Replacement Ascon MS3D roof sensor probe 25m long.
Roof Sensor Faults
"RRR" push display button and the "P" reading will be either "00" or "84".
If "00" there is an open circuit, look for a break in the wire or replace sensor.
If "84" or higher there is a short circuit - check wire or replace sensor.
Determine Sensors or Controller at Fault
Sensor - Swap sensors over - fault reading should change over to the opposite.
Controller - If it does not change over to opposite, new controller maybe required.
When purchasing, tap the edit cart link to see what freight you pay.
Be The First To Review This Product!
Help other Direct Pool Supplies users shop smarter by writing reviews for products you have purchased.